On account of Main transformer CT (current transformer)’s wrong connection leading to additional circuit, differential loop’s circuit is calculated according to transformer’s load status. Detail analysis is made. In conclusion, potential fault trip exists in RCS-978E stable ratio differential protection. Measures are brought forward to avoid fault trip, so that reliability of transformer protection is improved.
IOS Press, Inc.
6751 Tepper Drive
Clifton, VA 20124
Tel.: +1 703 830 6300
Fax: +1 703 830 2300 firstname.lastname@example.org
(Corporate matters and books only) IOS Press c/o Accucoms US, Inc.
For North America Sales and Customer Service
West Point Commons
Lansdale PA 19446
Tel.: +1 866 855 8967
Fax: +1 215 660 5042 email@example.com